The following family of extension cord sets have been designed with protection against water ingress:
XN515P-DF, XN520P-BF, XN615P-BF, XN620P-BF,XN515R-CF, XN520R-CF, XN615R-AF, XN620R-AF,XL515P-AF, XL615P-AF, XL715P-AF,XL515R-AF, XL615R-AF, XL715R-AF.
Aesthetically pleasing design with standard sizing to meet the requirements of NEMA WD 6. Both male and female connectors have inbuilt waterproof functionality, making the cord sets suitable for outdoor use. Sockets come with dust-proof and waterproof cover, which can prevent entry of dust and water droplets when not in use.
* This information was provided by
NINGBO XUANHUA ELECTRIC CO LTD
and may contain additional information outside the scope of this Claim Verification.
XL515P-AF, XL615P-AF, XL715P-AF, XL515R-AF, XL615R-AF, XL715R-AF, XN515P-DF, XN520P-BF, XN615P-BF, XN620P-BF, XN515R-CF, XN520R-CF, XN615R-AF, XN620R-AF
Marketing Claim Verified by UL Solutions
Plugs and connectors were submitted to tests for protection against solid foreign objects and tests for protection against water according to IEC 60529.
A. Measure and record all dimensional properties for the models to ensure compliance with manufacturer’s supplied drawings and authorization in ELBZ report (UL file E257089).
B. IEC 60529, Clause 13 Tests for protection against solid foreign objects indicated by the first characteristic numeral.
Level 4, effective against >1 mm. Most wires, slender screws, large ants etc.
C. IEC 60529, Clause 14 Tests for protection against water indicated by the second characteristic numeral.
Level 4, effective against Splashing water. Water splashing against the enclosure from any direction shall have no harmful effect, utilizing either: a) an oscillating fixture or b) A spray nozzle with no shield. Test a) is conducted for 10 minutes. b) is conducted (without shield) for 5 minutes minimum.
Water spray for 12 minutes, exceeding above requirements.
D. Dielectric Voltage Withstand Test in accordance with UL 817, Clause 11.4.
About the Company
NINGBO XUANHUA ELECTRIC CO LTD, No.58 GONGJI ROAD, SIMEN TOWN YUYAO, ZHEJIANG 315472 China.
Ningbo Xuanhua Electric Co., LTD., founded in 2004, specializes in the production of power cord, plug, rubber extension cord, wiring harness, coil and other wire and cable products, integrating design, research and development, manufacturing and sales. The company covers an area of 100 mu, building area of 150,000 square meters, strong professional and technical force, with modern production line and advanced testing equipment, the establishment of UL approved witness testing laboratory. Since its establishment, the company actively adopts national standards and advanced international standards organization production, and has passed ISO9001 quality system certification, ISO14000 environmental management system certification, BSCI social responsibility system certification. It has obtained the product safety certification of China CCC, UL/CUL, CSA, ASTA, PSE, VDE and other 24 countries. It has won the honorary titles of "Ningbo Famous Export Brand", "Ningbo Famous Brand" and "China Quality and Integrity Enterprise".
What is UL Verification?
UL Verification is an objective, science-based assessment that confirms the accuracy of marketing claims. Our independent assessment process scrutinizes the validity of specific advertising or promotional statements, giving you a way to separate verified fact from fiction.