* This information was provided by FURUKAWA TECHNO MATERIAL CO., LTD. and may contain additional information outside the scope of this Claim Verification.
3’2’’ char height, 12.0 m² total and 0.04 m total and 0.04 m²/s peak smoke release of PROTECO-TAPE per UL1685 for specific cable designs TAPE per UL1685 for specific cable designs
The bundled cable samples below were wrapped with either the sheet or tape product. The wrapped bundles were then loaded on the tray per UL 1685 “Standard for Vertical-Tray Fire-Propagation and Smoke-Release Test for Electrical and Optical-Fiber Cables” and flame tested. For Tape product testing, the bundled sample contained the following cables: - 600V CV3C 150Sch Power supply cable - FCPEV 30P Communication cable - CVV 30C Control cable Claim validity is extended only to the exact bundle configurations listed above.
Furukawa Techno Material , a Furukawa Electric group company, has been producing and supplying the finest products and materials for over 60 years. Our product lines include fire prevention materials and products used to protect wired cables and piping installations. Additionally, Furukawa Techno Material offers key techniques to prop up safety engineering for office, utility and plant buildings.
UL Verification is an objective, science-based assessment that confirms the accuracy of marketing claims. Our independent assessment process scrutinizes the validity of specific advertising or promotional statements, giving you a way to separate verified fact from fiction.