* This information was provided by Superior Essex International LP and may contain additional information outside the scope of this Claim Verification.
Cable part number PW52-Hxx-y8 (xx represents different packaging and y represents different jacket color)
Cable performance characteristics have been evaluated as outlined below to determine that the product satisfies the requirements of Sustainable Intelligent Building (SIB) Test Program for Type CMP PowerWise 1G cable part number PW52-Hxx-y8 (xx is for different packaging and y is for different jacket color). At Ambient (21C) Conditions: Data Rate Transmission per Bit Error Rate Testing | Single Cable Distance (meters) using Smart Bits Tester Performance 100 MB 200 1 Gb 160 10 Gb 120 Data Rate Transmission per HDBaseT™ transmission | Single Cable Distance (Meters) per UL 4299, Outline of Investigation for Performance Power Over HDBaseT™ (PoH) Cables HDBaseT 120 At LP 0.5A High Temperature (70.1C) Worst Case Conditions: Data Rate Transmission per Bit Error Rate Testing | Single Cable Distance (Meters) using Smart Bits Tester Performance 10 MB 200 100 MB 140 1 Gb 140 10 Gb 105 Data Rate Transmission per HDBaseT™ transmission | Single Cable Distance (meters) per UL 4299, Outline of Investigation for Performance Power Over HDBaseT™ (PoH) Cables HDBaseT 105 Maximum bundle size of 91 cables operating at 0.5A per conductor for a 15°C temperature rise at a 45°C ambient per TIA TSB-184A. (Editor’s note: Obtained from POE/LP data) HDBaseT™ transmission distance of between 80 – 100 meters per UL 4299, Outline of Investigation for Power Over HDBaseT™ (PoH) Cables, using a modular plug terminated link (direct connect) configuration at room ambient @ LP 0.5A. (Editor’s note: Ran single “cable Recommended cable” test per Valens POH) Power over Ethernet (PoE) delivery distance is as indicated for the PoE Type per DC resistance measurements in ANSI/TIA-568.2-D: Balanced Twisted-Pair Telecommunications Cabling and Components, and, the power source and powered device specifications in IEEE 802.3bt: IEEE Standard for Ethernet Amendment 2: Physical Layer and Management Parameters for Power over Ethernet over 4 pairs: Type CMP PowerWise 1G based on maximum power limits at the load (PD): Type 1 (15W): 378 m @ Ambient (21C) & 323 m @ LP 0.5A operating temperature Type 2 (30W): 236 m @ Ambient (21C) & 202 m @ LP 0.5A operating temperature Type 3 (60W): 236 m @ Ambient (21C) & 202 m @ LP 0.5A operating temperature Type 4 (90W): 237 m @ Ambient (21C) & 203 m @ LP 0.5A operating temperature Jacket Temperature Rating at least 90°C per UL Standard for Safety for Communications Cables, UL 444 test data Installation Type Designation: Type CMP per UL Standard for Safety for Communications Cables, UL 444 test data 1 Gb transmission (single cable) passive transmission performance per ANSI/TIA-568.2-D: Balanced Twisted-Pair Telecommunications Cabling and Components, from 1 MHz up to a maximum stop frequency of 450 MHz Power efficiency at an ambient temperature of 45 °C is 89.3%. Power efficiency at an ambient temperature of 70.1 °C (worst case) is 88.5%.
For over 90 years, Superior Essex has forged a path by meeting and exceeding the wire and cable requirements for the automotive, industrial, commercial, residential, energy and communications markets. We proudly trace our history back to 1930, when the Essex Wire Corporation was founded in Detroit, Michigan. Meanwhile, Superior Cable Corporation was founded in 1954, in Hickory, North Carolina. After many years of growth and change, in 1999, Superior TeleCom (formerly Superior Cable) acquired Essex International (formerly Essex Wire) and together they formed the company we are globally known as today – Superior Essex – now based in Atlanta, Georgia.
UL Verification is an objective, science-based assessment that confirms the accuracy of marketing claims. Our independent assessment process scrutinizes the validity of specific advertising or promotional statements, giving you a way to separate verified fact from fiction.